The introduction about socket weld pipe fittings
What is the socket weld pipe fitting?
A Socket Weld is a pipe attachment detail in which a pipe is inserted into a recessed area of a Valve, fitting or flange.
Comparing the butt weld pipe fittings, socket weld pipe fittings are mainly used for small pipe diameters ;commonly for piping of diameter less than 4 inch. Socket-welded joints construction is a good choice when high leakage integrity and great structural strength are important in the piping design .
To join pipe to Valves and fittings or to other sections of pipe, fillet-type seal welds be used. Socket-welded Joints construction is a good choice wherever the benefits of high leakage integrity and great structural strength are important design considerations.
Fatigue resistance is lower than that in butt-welded construction due to the use of fillet welds and abrupt fitting geometry, but it is still better than that of most mechanical joining methods.
Some details of Socket Weld pipe fittings
SW Fittings are family of high pressure fittings are used in various industrial processes.
- They are used for lines conveying flammable, toxic or expensive material where no leakage can be permitted, and for steam 300 to 600 PSI.
- They are used only in conjunction with ASME Pipe and are available in the same size range.
- They are used in areas where pipe-work is permanent and are designed to provide good flow characteristics.
- They are are produced to several ASTM standards and are manufactured in accordance with ASME B16.11. The B16.11 standard covers pressure-temperature ratings, dimensions, tolerances, marking, and material requirements for forged carbon and alloy steel. Acceptable material forms are forgings, bars, seamless pipe, and seamless tubes which conform to the fittings chemical requirements, melting practices, and mechanical property requirements of ASTM A105, A182, or A350.
- They are available in three pressure ratings: Class 3000, 6000 and 9000.
Types of socket weld fittings by class, size and wall thickness
Plugs and Bushings are not identified. They may be used up through Class 6000 NPS
Haihao Group Pipe Fittings for Socket Weld Pipe systems:
|Socket weld 90°Elbow||Socket weld 45° Elbow||Socket weld straight tee||Socket weld cross|
|This Elbows make 90° changes of direction in the run of pipe.||This Elbows make 45° changes of direction in the run of pipe.||This Tee makes 90° branch from the main run of pipe.||Crosses makes 90° branch from the main run of pipe.|
|Socket weld Full Coupling||Socket weld Half Coupling||Socket weld Reducing Coupling||Socket weld End Cap|
|A Full Coupling, joins pipe two pipe or to a nipple etc.||The Half Coupling can be directly welded to the run pipe, to make a branch connection.||The Reducing Coupling joints two different outside diameters of pipe.||Seals the end of pipe.|
|Socket weld Reducer insert||Socket weld Union(MSS SP-83)|
|Socket Weld Reducer Inserts are manufactured to MSS SP-79. They enable quick and economic combinations of pipeline reductions to be made using standard Socket Weld fittings.||It is a screwed joint design and it consists of three interconnected pieces: two internally threads and a centerpiece that draws the ends together when rotated. Unions should be screwed tight before the ends are welded to minimize warping of the seats.|
1.The pipe need not be beveled for weld preparation.
2.Temporary tack welding is no needed for alignment, because in principle the fitting ensures proper alignment.
3.The weld metal can not penetrate into the bore of the pipe.
4.They can be used in place of threaded fittings, so the risk of leakage is much smaller.
5.Radiography is not practical on the fillet weld; therefore correct fitting and welding is crucial. The fillet weld may be inspected by surface examination, magnetic particle (MP), or liquid penetrant (PT) examination methods.
6.Construction costs are lower than with butt-welded joints due to the lack of exacting fit-up requirements and elimination of special machining for butt weld end preparation.
The Disadvantages of Socket Weld Pipe Fittings:
1.The welder should ensure for a expansion gap of 1/16 inch (1.6 mm) between de pipe and the shoulder of the socket. ASME B31.1 para. 127.3 preparation for welding (E) socket weld assembly says: In assembly of the joint before welding, the pipe or tube shall be inserted into the socket to the maximum depth and then withdrawn approximately 1/16″ (1.6 mm) away from contact between the end of the pipe and the shoulder of the socket.
2.The expansion gap and internal crevices left in socket-welded systems promotes corrosion and make them less suitable for corrosive or radioactive applications where solids buildup at the joints may cause operating or maintenance problems. Generally require butt welds in all pipe sizes with complete weld penetration to the inside of the piping.
3.Socket welding are unacceptable for ultrahigh hydrostatic pressure in food industry application since they do not permit full penetration and leave overlaps and crevices that are very difficult to clean, creating virtual leaks.
The purpose for the bottoming clearance in a socket weld is usually to reduce the residual stress at the root of the weld that could occur during solidification of the weld metal, and to allow for differential expansion of the mating elements.
Haihao group have a nearly 30 years socket weld pipe fittings manufacture experience. we can supply suitable products as per your request. Besides these standard products, we also can supply customized butt welding pipe fittings accordingly.
We sincerely welcome customers domestic and abroad to visit us for cooperation and development.